Your air ducts are one of the most important systems in your home, and if the ducts are poorly sealed or insulated they are likely contributing to higher energy bills. Learn more about ducts below, courtesy of Denver’s favorite heating repair company, Blue Sky!
Your home’s duct system is a branching network of tubes in the walls, floors, and ceilings; it carries the air from your home’s furnace and central air conditioner to each room. Ducts are made of sheet metal, fiberglass, or other materials.
Ducts that leak heated air into unheated spaces can add hundreds of dollars a year to your heating and cooling bills. Insulating ducts in unconditioned spaces is usually very cost-effective. If you are installing a new duct system, make sure it comes with insulation.
Sealing your ducts to prevent leaks is even more important if the ducts are located in an unconditioned area such as an attic or vented crawlspace. If the supply ducts are leaking, heated or cooled air can be forced out of unsealed joints and lost. In addition, unconditioned air can be drawn into return ducts through unsealed joints.
Although minor duct repairs are easy to make, qualified professionals should seal and insulate ducts in unconditioned spaces to ensure the use of appropriate sealing materials.
Check your ducts for air leaks. First, look for sections that should be joined but have separated and then look for obvious holes.
Duct mastic is the preferred material for sealing ductwork seams and joints. It is more durable than any available tape and generally easier for a do-it-yourself installation. Its only drawback is that it will not bridge gaps over ¼ inch. Such gaps must be first bridged with web-type drywall tape or a good quality heat approved tape.
If you use tape to seal your ducts, avoid cloth-backed, rubber adhesive duct tape — it tends to fail quickly. Instead, use mastic, butyl tape, foil tape, or other heat-approved tapes. Look for tape with the Underwriters Laboratories (UL) logo.
Remember that insulating ducts in the basement will make the basement colder. If both the ducts and the basement walls are not insulated, consider insulating both. Water pipes and drains in unconditioned spaces could freeze and burst if the heat ducts are fully insulated be-cause there would be no heat source to prevent the space from freezing in cold weather. However, using an electric heating tape wrap on the pipes can prevent this. Check with a professional contractor.
Carbon monoxide (CO) detectors are required in new buildings in many states. They are highly recommended in homes with fuel-burning appliances such as natural gas furnaces, stoves, ovens, water heaters, and space heaters. An alarm signals if CO reaches potentially dangerous levels.
This Air Distribution System Design: Good Duct Design Increases Efficiency (PDF) fact sheet explains how good duct design increases efficiency of air distribution systems for central heating and cooling. The air distribution system may reach an efficiency of 80 percent or more for little or no additional cost, resulting in homeowner savings of $50 to $200 or more each year in heating and cooling costs. The fact sheet describes duct design objectives, types of supply duct systems (such as trunk and branch, spider, radial and perimeter loop systems) as well as return duct systems (including multiple-room return and central return systems), duct materials and duct and register locations. It also provides duct design methods, design recommendations and key design elements.
To schedule a heating system installation for your Arvada, CO, home, contact our team today!